BENTEL J424 MANUAL PDF
J – 8 to 24 Zone Expandable Control panel. FireClass J Details Manuals / Documents Approvals / Declarations of Conformity. MAIN FEATURES. BENTEL SECURITYsrl shall not assume the responsibility for damage arising from improper application or use. Manual Extinguishment Input. + Add to cart. Specification; Documents. Manufacturer. BENTEL. Part number. J Number of zones. 8. Zone expansion up to. Supply voltage. V AC.
|Published (Last):||28 April 2012|
|PDF File Size:||15.37 Mb|
|ePub File Size:||2.84 Mb|
|Price:||Free* [*Free Regsitration Required]|
Repeater for J and J panels
The J control panel is also available with a backlit display, which shows all the information regarding the control panel status. Detailed instructions for use are in the User’s Guide.
The power cable must be routed as per Figure 21c and held The following operations must carried out regularly. Connecting Call-points Figure 15 Wiring diagram of 3 detectors with Normally-Open Outputs and a Call point with zero ohm contact resistan – ce: Enter text from picture: Up to 1 A can circulate on the PR Output.
Bentel J Manuals
Time option Key 0respectively, to increase or decre PS Input of Extinguishment Mod. Lastmanuals offers a socially driven service of sharing, storing and searching manuals related to use of hardware and software: Press Enter or Esc to confirm and go back to the Main menu.
J Declaration of Conformity English. Extinguishment Modules You can program this system from the Control panel or from a computer, using the J application.
Bentel J424 Installation Manual
Page 12 Figure 2 Maximum configuration of the J Control panel Silence status will be signalled by: Designed and made according to EN54 and EN standards with JEXT extinguishment modulethe J is a microprocessor based control panel for medium and large applications. Disable Extinguishment Input [IE] terminals. Type Product name to find it. In any way can’t Lastmanuals be held responsible if the document you are looking for is not available, incomplete, in a different language than yours, or if the model or language do not match the description.
Fire panel sticker J424 – EN
This easy-to-use control panel is protected by a lockable frontplate which allows operational access to authorized personnel only. Telecom Mains Mains Disab.
Flat cable accessory item: Introduction 3k5 of IEC Installing Repeaters Installing Repeaters Installing the Control panel Work carefully through the following steps see the Fi – The Display Module if used must be installed be- gures on pages 10, 12 and Display Door screws Unless otherwise stated, the numbers in boldface in this Keyswitch Access Level 2 Page 15 Flat cable accessory item: Remove the screws 4 and open the Con- trol panel.
This manual also for: Table of Contents Add to my manuals Add. Connecting A Power Supply 60 and jumper connectors. Don’t show me this message again. Install the Extinguishment Module, as follows.
If you disable the Extinguishment Module during the Extinguishment Phase, the latter will be interrupted. Expander Modules Accessing the Programming session Enrolling: Button n Pre-extinguishment Phase n Manual Extinguishment If the programmed extinguishment conditions occur The Extinguishment Module can be activated from j44 – programmed by your Installerthe Extinguishment nual call-points ask your Installer for details.
Page of 64 Go.